Determining amount of heat withdrawn by the fan from the capacitor of small refrigerating machines
Авторы: Лемешко Михаил Александрович, Романов Павел Витальевич, Дмитриенко Надежда Алексеевна
Рубрика: 16. Новые технические решения
Опубликовано в
VI международная научная конференция «Технические науки в России и за рубежом» (Москва, ноябрь 2016)
Дата публикации: 08.10.2016
Статья просмотрена: 13 раз
Библиографическое описание:
Лемешко М. А., Романов П. В., Дмитриенко Н. А. Determining amount of heat withdrawn by the fan from the capacitor of small refrigerating machines [Текст] // Технические науки в России и за рубежом: материалы VI Междунар. науч. конф. (г. Москва, ноябрь 2016 г.). — М.: БукиВеди, 2016. — С. 8084. — URL https://moluch.ru/conf/tech/archive/228/11167/ (дата обращения: 17.12.2017).
The object of research is a heat transfer process in small refrigerating machines. We investigated the possibility of reducing specific energy consumption of a compression refrigerator by increasing the intensity of cooling of the refrigerant in its condenser.
The reduction of energy consumption of refrigeration equipment is very important problem to be constantly paid attention to during its rapid development, and at present time.
It is known [1] that it’s possible to intensify the process of condensation of the refrigerant in several ways:
− increase surface area of heat exchange;
− to increase the coefficient of heat transfer from the condenser surface to the ambient air;
− to decrease the total thermal resistance of heat transfer as the reduction of its components (private thermal resistance);
− to increase the temperature difference of heat transfer (mean temperature difference).
The heat transfer coefficient from the surface of the capacitor can also be increased by increasing the velocity of the air near the surface of the capacitor for example, when you use the fan [2, 3], or by using evaporative cooling surface condenser, [4, 5], or using movable capacitor [6, 7]. It is interesting to refer to the option of a cooling condenser and a compressor of the refrigerating unit simultaneously [8].
When you heat a solid surface with the help of gas medium in natural convective heat transfer the heat transfer coefficient is usually not more than 20–80 W/m^{2}∙grad. One of the commonly used methods of cooling the surface of the condenser is forced ventilation process.
To increase the intensity of condensation process of the refrigerant we can use the other methods, such as it presented in the publication [9]. The use of fan for cooling the surface of the condenser is widely used to display coolers, which use compact compressor condensing unit with one or two fans, usually the capacity of the fridge is over 400 liters.
Small refrigerators with relatively high refrigeration capacity traditionally used to apply traditional method of cooling the condenser with the help of natural convection, which is considered [1], to be the rational use of fan for cooling the condenser. However, papers [11], let us make a complement to this tradition using a new approach. It is proposed to use a thermoelectric Converter to produce electricity from the running compressor of the refrigeration unit. The use of the Seebeck effect will enable the heat generated by compressor refrigerating machines to be converted into electricity and the latter to be used for blowing the surface of the capacitor. Thus, the fan is not consumed electricity from the network, and it allows to improve the heat removal from the surface of the capacitor. The heat exhaust from the compressor is usually dissipated into the environment, complementing the heat from the condenser. Typically, the capacity of the exhaust heat from the working refrigerating machine more than power get cold. Great Park for refrigeration compression refrigeration equipment in the aggregate is very large dissipation to the atmosphere.
Materials and methods.
Consider the circuit for cooling the condenser of a small refrigerating machine with a fan let us solve the problem of determining the amount of heat discharged from the surface condenser during its blowing surface of a fan.
Fan capacity refers to the volume of air passing through the fan per unit time. For example, cm^{3}/min, or in the system. Suppliers of fans for personal computers measure the performance of the fan in cubic feet per minute (Cubic Feet per minute, CFM). The manufacturer, always specifies a characteristic feature of the fan. (1 foot cubed equals 28 320 cm^{3} = 0,02832 м^{3}, 1 ft^{3}/min = 28320 cm^{3}/min or 472 cm^{3}/sec.)
The air flow generated by the fan determines how much heat you can take from the condenser per unit of time.
We denote the total capacity of the heat load on the condenser .
Theoretically, the magnitude of this heat load can be obtained from calorimetric calculation of refrigeration cycle specific design of the refrigerator.
Let us denote the temperature difference on the condenser surface and the ambient air is .
Let the air mass m, which is supplied to the surface condenser, is heated by ∆T in time t. Then he transferred quantity of heat:
(1)
where c_p is the heat capacity of air at constant pressure. The dimension parameters:
, , c.
The volume of air supply per unit time characterizes the fan performance , which should ensure the rate of heat dissipation from the condenser is Qt per unit of time.
Express the mass of air using its density and volume:
Then, in unit time will be given heat:
(2)
,
.
Where flow rate of the air flow through the fan for discharging heat output .
Where:
(3)
For dimensions taken in the expression (1):
Or , or min
For fans with the specified performance СFМ, it is necessary to consider that 1 m3/min = 30,48 СFМ (cubic pounds per minute), or:
(4)
Results.
Substituting in the formula (3) the heat load on the condenser, temperature difference, density and specific heat of the air, you can calculate the capacity of the fan.
The actual performance of the fan for removal of thermal energy from the surface of the condenser Qt must be greater than calculated one due to partial scattering of the air flow when blowing the surface of the capacitor. This dispersion can be considered a design parameter – the coefficient of dispersion of blood flow. Depending on the shape of the air flow and the shape of the condenser the value of this coefficient may range from 0.5 to 0.9.
The actual performance of the fan:
(5)
Let consider an example.
Let the power, the exhaust from the condenser 60 W, the temperature difference between the surface condenser and the surrounding air is 25 0C.
For the approximate calculation accept density of air at t=25 0C and a pressure equal to one atmosphere: C=1100,0 j/kg·, then the data given by formulas (3) and (4), assuming Кр =0.6, one will get:
(6)
For relatively accurate calculations the humidity and the pressure in the measurement of fan performance must be taken into account. For humidity 60%, air density is approximately equal to 0,95 kg/m3.
Specific heat of air depends on air humidity. For dry air it is equal to .
Full heat capacity of moist air is the sum of the heat capacities of dry air and steam:
.
Specific heat capacity is usually referred to 1 kg of dry air:
, .
Then
.
where d is the moisture content of the air in kg/kg c. b.
Using the expression (6), we perform estimating calculations linking heat load on the condenser and fan performance. The results of the calculation are given in table 1.
To indicate air flow in CFM dimensions, from the expression (6), we get:
.
Here [W] = ft cube /min.
Table 1
Example calculation of fan performance
Q, Wat 


60 











20 
30 
40 
20 
30 
40 
20 
30 
40 

W, 
957 
643 
487 
1950 
1267 
975 
2925 
1950 
1462 
W, CFM 
0,034 
0,022 
0,017 
0,068 
0,044 
0,034 
0,103 
0,068 
0,052 
As can be seen, to ensure heat removal from the surface of the condenser by the fan airflow, for given surface temperatures of the condenser and the ambient temperature, it is necessary to create an air flow which is directly proportional to the dissipated thermal power. For example, if the heat load on the condenser has a capacity of 30,0 W, ambient temperature 25°C, the surface temperature of the condenser 45 °C, the diffusion flow Кр = 0,8, then the necessary airflow fan W must be equal to 861 cm^{3}/min. Or for cooler fan for PK cooling) W = 0,030 СFM.
Discussion and conclusion.
It would seem that airflow in 861 cm^{3}/min is not too much, so the airflow is able to provide even a relatively low powerful fan. However, you must keep in mind that the airflow generated by the fan and the airflow blown from the surface of the condenser is not the same thing. If the fan is installed in the housing of the refrigerator or fan is included into a condensing unit, its performance will differ from that specification in the technical documentation.
It is known that specification given in the documents states the fan capacity can be calculated under ideal conditions, in the absence of resistance it creates the air flow. In real conditions the path of the air flow generated by the fan, have always some obstacles that reduce the volume of pumped air through the fan per unit time, and increasing the difference between the pressure of the air flow generated by the fan, and the pressure of the environment (atmospheric pressure).
In the General case, we can assume that the static pressure of air flow from the fan is a function of the speed of the fan: . This function is called the characteristic curve or the flow characteristics of the fan.
Table 2
Here are some examples of fans that can be used to cool condensers in domestic refrigerators
Name 
Dimensions mm 
Power, W 
Speed rev/min 
Performance, CFM 
Performance cm3 / min 
Noise dB 
Pricerub. 
KDE1204PFV2 
40x40x10 
1 
5800 
7 

27 
230 
KDE1205PFV2 
50x50x10 
1,1 
4300 
11 

26 
370 
KDE1209PTB1 
92x92x25 
1,8 
2800 
49 

34 
320 
PMB1275PNB1.AY 
75x75x30 
3,6 
3400 
13,6 

43,5 
560 
PMD1209PTB1.A(2) 
92x92x25 
5,5 
4200 
77 

48 
490 
Thus, the calculations show that the heat removal from the condenser of the refrigeration machine with the use of modern fan it is advisable to perform a design of small refrigerating machines with a smaller condenser, but they must be equipped with a fan for cooling the condenser.
The use of heat from the compressor for additional power source can solve two problems: a heat sink energy from the compressor to convert this energy into electricity.
In this case, fans are recommended to cool the condenser and increase the intensity of cooling will provide improved performance of the refrigeration cycle and, ultimately reducing the average energy consumption of the refrigeration machine.
We have also proposed to increase the power of the fan and its rational use to provide a refrigerator battery. This will allow us using low thermal load on the unit, to accumulate energy, and when load is increased (e.g. when loading the refrigerator Cabinet products) – it is effective to intensive heat sink, reducing the overall power consumption of the refrigerator.
References:
 Weinberg B. S., Household compression refrigerators / S. B. Weinberg, L. N. Vine. — M.: Food industry, 1974. — 272.
 Lemeshko M. A., the Dependence of energy efficiency of a compression refrigerator to the method of cooling of its condenser / Lemeshko M. A., Kozhemiachenko A. V. Urunov S. R. // Technical and technological problems of service — SaintPetersburg: SPGEU — 2014 — № 4(30). S. — 58–60.
 Lemeshko M. A. increasing the intensity of heat exchange processes of the capacitor compression refrigerator /basic and applied researches: challenges and results. 2014, no.12. S. 65–69.
 Lemeshko M. A. the Use of evaporative cooling to increase the energy efficiency of household refrigerator / Lemeshko M. A., Urunov S. R., Golovina, E. I. // Journal of scientific publications graduate and doctoral students. Kursk, 2015 — № 1(103). — PP. 114–116.
 Lemeshko M. A., Dmitrienko N. A. Urunov S. R. study of the effectiveness of the evaporative condenser of the compression refrigerating mAtires/ interdisciplinary Institute for Science and education. 2014. No. 6. S. 48–51.
 The patent for invention RUS 2570533 29.12.2014. Household refrigerator with movable condenser / Lemeshko M. A., Kozhemiachenko A. V., S. R. Urunov.
 Lemeshko M. A., Alekhin S. N., Urunov S. R., Serebryakov A. V. Household refrigerator with a movable condenser./A young scientist. 2016. № 6 (110). S. 122–127.
 Kozhemiachenko, A.V., Lemeshko M. A., Rugasevic V. V., V. B. Sherstyukov Reducing energy consumption of household refrigerating appliance by inteneficacia cooling condenser / Engineering journal of don — 2013. Vol. 24, № 1(24). S. 60–64.
 Lemeshko M. A. Technology energy efficiency of household refrigerating appliances. / Fundamental and applied researches: challenges and results. 2014. № 13. P. 188–196.
 The patent for invention RUS 2521424, 12.03.2013. The cooling method of the capacitor compression refrigerator. / Lemeshko M. A., CogemaChenko A. V., Rugasevic V. V., Sherstyukov V. V., Romanova, M. I., Deineka I. G.
 Lemeshko M. A., Alekhin S. N., Urunov S. R., Serebryakov A. V. Method of increasing the energy efficiency of household refrigeration appliances. / In the collection Nike: the scientific search in a modern world the collection of materials of XI international scientificpractical conference. 2016. P. 33–36.
Обсуждение
Социальные комментарии Cackle